A. This fireplace has a pilot which must be lit manually. When lighting the pilot, follow these instructions exactly.
B. BEFORE LIGHTING, smell all around the fireplace area for gas. Be sure to smell next to the floor because some gas is heavier than air and will settle on the floor.
C. Use only your hand to push in or turn the gas control knob. Never use tools. If the knob will not push in or turn by hand, do not try to repair it; call SUNDANCE Energy for a qualified service technician. Applying force or any attempted repair may result in a fire or explosion.
D. Do not use fireplace if any part has been under water. Immediately call SUNDANCE Energy to inspect the fireplace and to replace any part of the control system and any gas control which has been immersed.
STOP! Read the safety information above.
Turn off all electrical power to the fireplace.
For MN/MP/TN/TP applicances only, go on to Step 4. For RN/RP appliances, turn the On/Off switch to the "Off" position or set thermostat to lowest level.
Open control access panel.
Push in gas control knob slightly and turn clockwise to "Off."
Wait five (5) minutes to clear out any gas. Then smell for gas, including near the floor. If you smell gas, STOP! Follow "B" in the safety information above. If you do not smell gas, go to the next step.
Remove glass door before lighting pilot.
Visibly locate pilot by the main burner.
Turn knob on gas control counter-clockwise to "Pilot".
Push the control knob all the way in and hold. Immediately light the pilot by repeadedly depressing the piezo spark ignitor until a flame appears. Continue to hold the control knob in for about one (1) minute after the pilot is lit. Release knob and it will pop back up. Pilot should remain lit. If it goes out, repeat steps 5 through 8.
If knob does not pop up when released, stop and immediately call SUNDANCE Energy.
If after several tries the pilot will not stay lit, turn the gas control knob to "off" and call SUNDANCE Energy.
Replace gas door.
Turn gas control knob to the "On" position.
For RN/RP appliances, turn the On/Ofrf switch to "On" position or set thermostat to desired setting.